Key criteria in the selection of AirMaster units were the ability to attenuate external noise and to provide a high standard of filtration of incoming air. Other factors which were considered were demand control of air quality, low casing break out noise and good draught control in wintertime.
“The rooms are used almost every evening for scouting activities, meetings and training; and from September 2017 there will be a nursery here from 8am to 6pm every weekday,” explained Premises Manager Martin Linsey. “Because of our location on the busy Holloway Road with its high noise and air pollution levels, there are no opening windows. However, there was a requirement for efficient mechanical ventilation,” he added.
Four AirMaster units with ORBIT control panels have been installed in the building, with carbon dioxide sensors to monitor indoor air quality and modulate ventilation rates according to occupancy. This arrangement ensures optimum energy efficiency, further enhanced by EC inverter controlled fan motors.
The AirMaster units have Class M5 filtration of both incoming and outgoing air, minimising ingress of outdoor pollutants and protecting the heat exchangers from fouling. Noise attenuation of at least 49dB minimises intrusion of external traffic noise, whilst the quiet running of AirMaster (just 35 dB(A) at 1 metre) ensures the units do not disturb meetings or other activities.