Control using CO2 sensors
CO2 control is an excellent method for managing the indoor air quality in places of learning, such as schools, academies and universities. An indoor environment with good air quality could be expected to have a CO2 concentration of between 500 – 750 ppm, which poses no issues to mental function. However, studies have shown conclusively that high levels of CO2 (anything above 1,000 ppm) have an adverse effect on students’ ability to concentrate and take decisions (eg, Fisk & Mendell, Berkeley Lab – Univ of California, 2012). Beyond 2,000 ppm students experience noticeable drowsiness.
CO2 sensors for AirMaster air handling units with demand controlled ventilation are compact and can be wall-mounted or integrated within the casing of the direct ventilation unit. Their operating range is between 0 – 2,000 ppm (= 0.002% by volume). Crucially, they can be used for modulating control of the heat recovery ventilation system. Typical set values for a CO2 sensor are Minimum CO2 = 500 ppm (for the initiating signal) and Maximum CO2 = 1,500 ppm (for full throughput).
Demand controlled ventilation using carbon dioxide (CO2) sensors is essentially a combination of two technologies: sensors which monitor CO2 levels in the air inside a building and an air handling unit (AHU) that uses data from the sensors to regulate the amount of ventilation air admitted.
CO2 sensors can be paired with a ‘base’ level of direct ventilation. In this mode, the heat recovery ventilation unit is programmed to run continuously at low load, until a signal from the sensor indicates that air quality has begun to change. As long as the CO2 level remains above the minimum threshold, the AirMaster heat recovery air handling unit continues under modulating control.
To prevent stop/start cycling around the CO2 entry level, the start point is automatically programmed to ‘lower limit + 10%’. The stop signal is generated at the lower limit exactly.
From an energy saving perspective, CO2 control makes a great contribution by preventing losses incurred through over-ventilation, without compromising on consistency of good indoor air quality.
The potential of CO2 sensors and demand controlled ventilation for operational energy savings is considerable.. The highest payback can be expected in auditoriums, schools, meeting rooms, shopping centres and other spaces in which occupancy is variable and unpredictable and in areas with high utility rates.
Permanent Infra Red (PIR) motion sensors provide signals which can be used for start /
stop control of heat recovery ventilation units. The sensor controls respond to minute increases of infra-red radiation emitted from within its field of vision, which are then interpreted in terms of human movement. Sensors have uniform detection sensitivity within a range of 0.5 – 12m. Their circuitry includes a true motion algorithm, which allows the sensor to distinguish between (a) the motion of a room occupant
and (b) other factors arising from infra-red sources, but without any corresponding displacement. Care needs to be taken with the mounting of PIR sensors, to avoid spurious signals resulting from the effects of sunlight, electric circuits and fan-operated HVAC systems.
PIR devices can be programmed to operate with an ‘over-run’ timer. This instructs the heat recovery ventilationunit to continue
in operation for an over-run period (say, 30 minutes) after the last detected movement, and then switch itself off. This feature of PIR control contributes to reducing energy usage, by ceasing direct ventilation when not required.
Alternatively, it may be desirable to have a programmed level of ‘base’ ventilation. The PIR signal (to confirm that people have entered the room) is then used to switch the heat recovery ventilation unit up to full throughput. Once the last person has left, the over-run period counts off, followed by reversion to base load.
Please note, there is more content for this, which is normally concealed, but can be revealed by selecting the arrow.
AirMaster heat recovery ventilation units can be used to monitor and control relative humidity (RH). This can be achieved with AirMaster hydrostats, which have a humidity measuring element of stabilised synthetic gauze. The measured variable is fibre length, which is proportional to the surrounding RH. Hydrostats can be used with either minimum or maximum settings, with accurate operation within the range 25 – 95% RH.
Hydrostats are suited to systems designed to have a base level of ventilation, with the ‘dehumidify’ signal being used to take the heat recovery ventilation unit to full power. This combination works well in facilities such as sports and leisure centres.
For heat recovery ventilation to operate with the lowest energy usage, the choice of sensor is crucial. Whether the installation is for a classroom, meeting room, reception area, individual office or treatment room, typical usage patterns can be anticipated and sensor selection made accordingly. SAV are happy to advise the type and positioning of sensors for any type of project. Our objective is to hold ventilation flow only to what is required and thereby minimise carbon footprint. To investigate the potential of heat recovery ventilation for your project(s), please contact us either:
by phone: 01483 771910
by e-mail: [email protected]